By Gary Forbes
Gary is the data center solutions specialist, part of WESCO's Data Communications Emerging Technologies division. His team is a technical resource for internal departments and customers in all things datacom.
Data center cooling has traditionally been tackled one way. Air conditioning units (or CRACs) are placed around the outside wall of the room and aligned with the hot aisle. They then pump cold air underneath a raised floor for distribution in the cold aisle. While this method is generally considered an effective technique, it has a big limitation. It makes air travel long distances through open spaces between the CRAC and the equipment needing cooling. This contributes to inefficiency.
Current developments in the data center air conditioning field center around limiting the distance that air has to travel and confining the space in which it is traveling. The goal is to prevent hot and cold air mixing and limit the amount of energy needed to distribute air throughout the data center.
Here are four alternative cooling methods you can implement in a data center to increase efficiency.
Method 1: In-Row Cooling
In-row cooling is one of the newer cooling strategies being deployed in data centers throughout the world. In-row cooling replaces a rack in the row with an air-handling unit. This creates a shorter and more predictable air flow path. In most cases, it eliminates the need for raised floors. Hot air leaving IT equipment is immediately captured by the air-handling units. It’s then cooled and dumped back into the cold aisle. In-row cooling uses the traditional hot-aisle/cold-aisle setup you find in most data centers. Best of all, this method is easy to retrofit into most environments as a replacement or supplement to traditional CRAC units.
Method 2: On-Rack Cooling
Another evolution in cooling technology is on-rack cooling (also known as back-of-rack or rear-door-replacement). This method replaces the back doors of an enclosure with a heat exchanger. This brings the cooling even closer to the heat source than in-row cooling. Hot air leaving IT equipment is never allowed to leave the enclosure before it’s cooled. A unique feature of this cooling method is that it eliminates the need for a hot-aisle/cold-aisle row arrangement in a data center. Because hot air never enters an ambient space, there’s no need to worry about preventing the mixing of hot and cold air. New versions of this technology allow for modular capacity scaling to more closely match the rack density.
Method 3: Heat Wheel
One of the newest technologies adopted in data centers involves a heat wheel. Large rotating wheels bring outdoor air into the environment for distribution under a raised floor in a traditional hot-aisle/cold-aisle arrangement. This same wheel also captures the hot air from the data center, eliminating the heat and expelling the exhaust outdoors. Because it eliminates heat, very little outdoor air is required and little mechanical energy is needed to cool the environment. Since these tend to be among the most energy-efficient cooling products, they are being adopted by more energy-conscious data center operators.
Method 4: Self-Contained Rack Enclosures
As rack densities in closets increase, self-contained rack enclosures are gaining popularity. These rack enclosures have built-in air conditioning that allows IT cabinets to exist in environments not designed as data center space. Recent developments in this technology have allowed for higher capacities, built-in fire suppression, and integration with DCIM and building management systems.
Smarter Cooling Methods
As data centers face increasing demands, greater efficiency is becoming more and more important. By investing in alternative cooling methods, data center operators can reduce inefficiencies without breaking the bank.
In this article: Data Communications
When it comes to handling hazardous chemicals, workers need the proper equipment to stay safe. Protecting a worker’s face and head should be an employer’s top priority. And while many businesses supply safety equipment, it’s not always used in the right way. A faceshield doesn’t provide the coverage necessary to prevent injury 100 percent of the time. Workers need to wear personal protective equipment (PPE) that protects both the eyes and the face from injury. A faceshield alone doesn’t always guarantee safety.
Efficiency on a lighting project is critical to profitability. Contractors seek ways to save time and money — particularly on labor costs — to ensure maximum profitability from every job. While lighting installations come with their own set of challenges, properly managing material can save time and ultimately increase job profitability.
Over the last decade, rapid improvements in lighting technology coupled with a focus on energy conservation backed by legislation have resulted in a noisy marketplace. Consumers are inundated as big brands compete every day to get their latest products and statistics online.
As consumer demands on networks increase, more businesses are turning to Category 6A cabling for their network infrastructure. This decision is primarily being driven by affordable price, high quality, and exceptional performance. Here are five reasons why you should choose Category 6A cable for your enterprise applications.
While sensors have long played an important role in industrial settings, the intersection of market forces in manufacturing with the Internet of Things (IoT) has recently propelled sensor technology to new heights. Coupled with greater network connectivity and improved machine learning, sensors are now more vital than ever as manufacturers search for ways to optimize value throughout all levels of operation.